NG900 & OG93 |
Vintage Models |
Clubs & SOC |
Other Cars |
Books Movies & Music |
What's New |
Photo of the Month |
that you are correct about the end of the run.
I'm going to run a new wire from the last good fixture and see if that works, it was late last night and I didn't check the fixture to see if I had continuity between ground/hot or ground/neutral.
I've run plenty of circuits in the past, this is the first one I've had that caused problems.
I'm just glad I checked it before the board and plaster guy did his thing!
posted by 64.61.4...
Posts in this Thread:
Members can receive an alert when someone posts in this thread.
- Electrical short during remodeling (long), Don , Mon, 4 Jun 2012 17:43:54
- Switch to nuetral short?, Tootsacolta, Mon, 4 Jun 2012 19:13:04
- Re: Electrical short during remodeling (long), LI_Dave, Mon, 4 Jun 2012 18:55:06
- can you draw and post circuit?, nuotatore, Mon, 4 Jun 2012 18:50:24
- Re: Electrical short during remodeling (long), Snowmobile , Mon, 4 Jun 2012 18:20:07
- Re: Electrical short during remodeling (long), TML, Mon, 4 Jun 2012 17:55:44
Post a Followup
This is a moderated bulletin board - Posting is a privilege, not a right.
Unsolicited commercial postings are not allowed (no Spam). Please, no For Sale or Wanted postings, SERIOUSLY.
Classifieds are to be listed in The Saab Network Classifieds pages.
This is a problem solving forum for over 250,000 Saab owners, so expect to see
problems discussed here even though our cars are generally very reliable. This is not an anything goes
type of forum. Saabnet.com has been a moderated forum since 1988. For usage guidelines, see the
Saabnet.com Mission and Purpose Page. Please remember that you are
not anonymous. Site Conact |
Your address is: 22.214.171.124 - Using CCBot/2.0 - Logged.